Fireus Pipe Wraps seal closed flammable pipes from 55mm to 160mm diameter and are located inside a wall or floor structure.
Fire rating up to 4 hours.
Intumescent is totally unaffected by water.
Intumescent is robust, ‘non-flaking’ and difficult to tear.
Identification on each product for full traceability.
Simple to use, easy to install.
Suitable for fitting to:
Concrete, masonry, porous concrete wall constructions.
Concrete floor constructions
Waste water and fresh water PVC pipes
Tested to BS476 Part 20:1987 and other International Standards.
Health and Safety
According to 91/155/EEC Revision No.1.
A comprehensive design, advice and support service is offered to architects, specifiers and contractors ensuring trouble free installation.
1. The wall or floor must be of solid construction. The recess hole must be the correct size. See table above.
2. Fix wrap around the pipe using adhesive tab and slide along pipe into wall/floor cavity to a depth of 5mm min./10mm max.
3. After insertion the cavity around the pipe can be made good with filler. The surface can then be decorated.
4. The identification label should be attached to the pipe to show a wrap has been fitted.